Conventional Fire Alarm Control Panel: ZD1000 automatic fire alarm system-typically made up of smoke detectors, heat detectors, manual pull stations, audible warning devices, and a fire alarm control with remote notification capability-can provide early warning of a developing fire.
The ZD1000 is a 4-zone to 16-zone FACP (Fire Alarm Control Panel), which uses conventional input devices. The panel accepts water flow devices, two-wire smoke detectors, four-wire smoke detectors, pull stations and other normally-open contact devices. Outputs include four Notification Appliance Circuits (NAC, SOUND1-4), three standard Form-A relays (alarm, trouble and supervisory) and an EIA-485 port to interface with remote annunciators and optional remote relay modules. The FACP is field programmable via the panel keypad. It also supervises all wiring, AC voltage and battery level.
|FACP||Number of Detection Zones||Number of Sounder Outputs||Output Delay Settings|
ZD1000-8: 16 Zone, 2 Sound Output
ZD1000-8: 8 Zone, 2 Sound Output
ZD1000-4: 4 Zone, 1 Sound Output Features:
- 4,8,16 Class B Initiating Device Circuits (IDCs)
All zones accept conventional detectors and any normally open contact device
- Four Class B Notification Appliance Circuits (NACs)
- One Form-A Alarm Relay
- One Form-A Trouble Relay
- One Form-A Supervisory Relay
- 3.0 amps of system power
- Max 20 conventional detectors in one zone.
- Auto/Manual mode setting enable walk test.
- Each Zone can be disabled,
- Sound output can be disabled.
- Manual active sound output enabled.
- Designed with standby batteries and space provision for two sealed lead-acid batteries.
- Testing and disable functions.
AC Power : 220 VAC, 50 Hz, 2.3 amps
Wire size: minimum #14 AWG (2.0 mm2) with 600V insulation
Battery (lead acid only)
Maximum Charging Circuit: Normal Flat Charge-27.6V @ 0.8 amp
Maximum Charger Capacity: 18 Amp Hour batter
Sound Output Device Circuits
General Alarm Zones 1 through 16
Operation: All zones Class B
Normal Operating Voltage: Nominal 24 VDC (ripple = 100 mV maximum)
Alarm Current: 15 mA threshold
Short Circuit Current: 42 mA maximum
Maximum Loop Resistance: 100 ohms
End-of-Line Resistor: 4.7K, ½ watt
Detector Loop Current is sufficient to ensure operation of two alarmed detectors per zone
Standby Current: 7.26 mA
Three Relays Output
Relay contact rating: 2.0 amps @ 30 VDC (resistive), 2.0 amps @ 30 VAC (resistive)
Nonresettable 24 VDC Power
Maximum ripple voltage: 10 mVRMS
Operating Voltage nominal 24 volts
Total DC current available from this output is up to 500 mA
Recommended maximum Standby current is 150 mARelated Products: